Due to the current economic climate, we are reviewing our pricing and as such, online ordering and pricing is currently unavailable, we apologise for any inconvenience this might cause.
Processor SINGLE LINK
The HomeWorksR QS processor provides control and communication to HomeWorksR QS system components. The Ethernet link allows communication to the HomeWorksR QS software, integration with third-party systems and communication between multiple processors. HomeWorksR QS processors may be connected using either standard networking or using ad-hoc networking. All processors on a project must be connected to a single network. The HomeWorksR QS software and all integration equipment must be connected to the same network as the processors.
The processor is powered from the QSPS-DH-1-75 power supply. Refer to the HomeWorksR QS
software to determine link power requirements. The HomeWorksR QS processor can be installed in an HQ-LV21, L-LV21, L-LV14, PNL-8 enclosure or DIN panels with control compartments (PDx-36 or PDx-64).
Each HomeWorksR QS 1-Link processor has one
link that can be configured as one of four types:
• HomeWorksR QS Power Panels 16 interfaces / 256 zones
• HomeWorksR QS Wired Device Link 99 devices / 512 zones
• HomeWorksR QS RF Link 99 devices / 100 zones
• HomeWorksR H48 Wired Dimmers 4 interfaces / 192 zones
Power Processor (P): 24–36 V- 250 mA maximum
Typical Power Consumption; 5 W; 8 Power Draw Units (PDUs)
Test conditions: Ethernet link connected, and device link in use
Regulatory Approvals Complies with: UL508, CSA – C22.2 No.14, IEC / EN 60669, NOM
Environment; Indoor use only. 32 °F to 104 °F (0 °C to 40 °C), 0% to 90% humidity, non-condensing
Heat Generated; 17 BTU/hr — typical (24 BTU/hr maximum)
Cooling Method; Passive Cooling
Power Failure Memory; System data stored in non-volatile memory. Timeclock retention for 10 years
Internal Timeclock; ±1 minute per year
Miswire Protection; All terminal block inputs are over-voltage and miswire protected against wire reversals and shorts.
Low-Voltage Link Wire Type; Two pair — one pair 18 AWG (0.75 mm2), one pair 18 to 22 AWG
(0.34 to 0.75 mm2) twisted shielded — IEC PELV / NECR Class 2 cable
Low-Voltage Power Wire Type; 18 AWG (0.75 mm2)
Communications; Ethernet, RS485 (QS, RF, Power Panel)
Link Capacities; HomeWorksR QS Power Panel Link 16 interfaces/256 zones
HomeWorksR QS Wired Device Link 99 devices/512 zones
HomeWorksR QS RF Link 99 devices/100 zones
HomeWorksR H48 Wired Dimmers 4 interfaces/192 zones
ESD Protection; Meets or exceeds the IEC 61000-4-2 standard
Surge Protection; Meets or exceeds ANSI/IEEE C62.41 standard
Mounting; Mounts in HQ-LV21, L-LV14, L-LV21, PNL-8 enclosure or DIN Panels with Control Compartment (PDx-36 or PDx-64)
Dimensions; With terminal blocks (as shown): 4.27 in (108 mm) x 5.63 in (143 mm)
Without terminal blocks: 4.27 in (108 mm) x 5.26 in (134 mm)
Connections; One 5-pin removable terminal block* for Link 1. One RJ45 standard Ethernet connection. *Each terminal will accept up to two 18 AWG (0.75 mm2) wires.